|How to add a new FBox?||2019-03-29|
Open the FBox Client, register/login the account, add FBox to the “+” at the bottom of the left title bar, and enter the serial number and password on the label attached to the FBox to add the FBox under your account. Under the condition that the FBox is powered on line, Configuring the FBox or other operation is available. For detailed operation, please refer to the FBox series product manual.
|Use FBox and FLEXEM PLC to realize communication and transparent transmission||2019-03-27|
FBox client software, remote download, device management, com1 port configuration and communication settings of FLEXEM PLC. Select FLEXEM Modbus, and the communication settings by default in the driver are OK . The FLEXEM Modbus protocol is selected in the PLC software, and the communication settings are consistent with the FBox side. In the FBox client software, data monitoring, add the address of PLC, can read the data that means normal communication. After the communication is normal, click on the “remote download” and pass it through the transparent transmission. After clicking through the transparent transmission, if it has not been transparently transmitted before, the virtual serial port will be automatically installed, the virtual serial port number and the word "transparent is ready" will be display. Open the PLC software, in the tool, communication parameter settings, select the serial port, is the virtual serial port number com1 installed on the FBox side, the communication parameter settings are the same as in the PLC communication settings. Then click on PLC, download the program, and download the program to PLC.
|FBox as host communication settings||2019-03-27|
When FBox is as the host station, in the FlexLogic software, system settings, serial port settings, select the user-self defined protocol. Then set it by modbus command. Specific cases can be supported by technical support.
|PLC as slave communication settings||2019-03-27|
In FlexLogic software, system settings, serial port settings, select FLEXEM Modbus protocol or compatible with FX2N slave protocol. Set the communication parameters. Select FLEXEM Modbus protocol to support FBox transparent transmission.
|PLC analog input and output point corresponding value range||2019-03-27|
3*PT100??????? AI0-AI2???Actual temperature*10 2*Current input?????AI3-AI4???Range（0-20000 represent 0-20ma） 1*Current output?????AQ0??????Range（0-20000 represent 0-20ma） If it is 4-20ma, the corresponding range is 4000-20000.
|What we can do if FLink can't use gadget configuration?||2019-03-27|
If the 6000 series wants to support flink and corresponding configuration tools, please ensure that the kernel version number is greater than or equal to 278, and the floader version is greater than or equal to 527. Just update the kernel with FStudio software version 8322 and above.
|The 6000 series on the hand does not support FLink, how to deal with the function?||2019-03-27|
To use the FLink function, use the FStudio software version 8322 and above, use it after updating the kernel.
|19.Use RW or recipe register, re-power on after power off and find that the data is not saved. Why?||2019-03-27|
RW or recipe data, etc., when the power is off, if the power is suddenly turned off, the data will be lost in the last few seconds to one minute. SRB17 can be set to on by using system register SRB17. It will be written immediately when power is lost, and will be saved every time once whenever it changes. No data will be lost.
|Is the administrator authority the highest in user rights? Is it possible to operate all the privileged com…||2019-03-27|
A: User rights don't be divide to high or low. Only users to the corresponding rights can operate on components that need corresponding permissions; but a user can have multiple permissions at the same time.
|Can the user level be logged off?||2019-03-27|
No, but you can force the current password level to be modified. Note that you can only switch from a high level to a low level. SRW105, occupying 1 word. SRW105 writes 0, which can be understood as logout.
|How to achieve multilingualism?||2019-03-27|
Step 1. Global Settings - Language Settings; Step 2. Use the text library for all the tags used in the project; Step 3. Modify the current language number, SRW10050, save when the power down. 0 means use language 1, 1 means use language 2, and so on. Word setting switch can be added to the project
|How to set up serial communication with PLC and other devices?||2019-03-27|
Add the corresponding driver in the communication connection, and set the communication parameters, pay attention to set the same as the device side setting such as PLC. Communication line connection: Method 1. COM port setting page, there is a big box "Connection Description" below, click to enter the connection description interface. Method 2. Open the software-help-online help-3 communication connection description.
|Communication connection - COMX-connected device as the master device, the host station number, slave statio…||2019-03-27|
The Host station number is the station number of the screen; the preset station number is the station number of the connected device.
|What alternatives do the “inching” buttons use?||2019-03-27|
Switch - reset. Reset: This is the inching property. During operation, when your hand always pressed the button, the bit address is always ON, and when the hand left, it immediately becomes OFF.
|Is the week in the system time displayed in Chinese?||2019-03-27|
Use the word status indicator, address SRW7, and status 7. The label of 0 corresponds to Sunday, and 1-6 corresponds to Monday to Saturday.
|What is the difference between system time and NTP time?||2019-03-27|
The system time is the time of running this computer, only in this time download will be brushed in. The NTP time is that if the HMI can access the external network, the network time will be automatically synchronized after the program is finished. Connected to the external network, similar to the mail receiving and receiving function of the touch screen. From the router's networking line to the touch screen, hmi's access to the NTP server (this is a standard time server) from the IP assigned to the HMI will automatically synchronize the time.
|Which register is used to store the system time in the touch screen, can it be modified?||2019-03-27|
The system time uses SRW0-7 to indicate the year, month, day, hour, minute, second, millisecond, and week; the time can be modified, just change the value of the corresponding register;
|How to change the touch screen time?||2019-03-27|
Enter the setup interface - Universal Time - Settings to modify the time.
|How to enter the settings interface?||2019-03-27|
Power on the touch screen, while holding down any point on the screen, until the “Click to operate” interface appears, click “Settings” to enter the setting interface.
|How to shield communication error prompts?||2019-03-27|
Communication prompt mask bit (SRW496.1 is ON for masking communication timeout prompt, SRW496.2 masks communication error prompt); Add timer in common window, trigger condition - trigger when window is open; End condition - Stop when window is closed; Timing Function - Set to check "Use bit index of word register" to turn SRW496.2 ON.